Schneider Electric (Australia) Pty Limited—230DRAS1MI and 230DRAS2MI Meter Boxes
What are the defects?
4CB163/6 Meter Isolator fitted in the 230DRAS Meter Box, may have the incorrect screw fitted on the lockout plate, causing electrical contact between the screw and metal bobbin assembly.
What are the hazards?
A screw on the side of the meter isolator may be electrically live. There is a risk of electric shock if contact is made with this screw.
What should consumers do?
If consumers have had electrical installation work carried out at their home or premises from January 2015 to July 2015 they may have had an affected product installed. They should contact Clipsal Direct on Tel # (1300 733 907) with full details so a replacement meter isolator can be organised as soon as possible. Consumers should not attempt to inspect or assess products themselves. For further information on the recall, and on how customers can organise a replacement circuit breaker please see www.clipsal.com/230DRASrecall.
- 1 January 2015 - 1 July 2015
Recall advertisements and supporting documentation
Office of the technical regulator (SA) is the responsible regulator for this recall.