Total Tools—Detroit Generator(s)
What are the defects?
Manufactured with a Multiple Earth Neutral (MEN) link between the neutral & earth without a Residual Current Device (RCD), which is non-compliant with safety clause 6 of AS2790 Electricity generating sets.
What are the hazards?
If a fault occurs in the unit or equipment the MEN, which is bonded to the frame, can cause the frame to become live with electrical current possibly causing an electric shock.
What should consumers do?
Cease using the product immediately. Customers should return their unit to the Total Tools store where purchased for rectification of the defect.
37 Total Tools franchised stores
Recall advertisements and supporting documentation
Energy Safe (VIC) is the responsible regulator for this recall.