Saber 7.5kVA / 7500W Generator
What are the defects?
Manufactured with a Multiple Earth Neutral (MEN) link between the neutral & earth without a residual Current Device (RCD), which is non-compliant with safety clause 6 of AS2790 Electricity generating sets. In addition, the Circuit Breaker Switch for Equipment (CBE) is single pole, which is non-compliant with safety clause 6.1.4.
What are the hazards?
If a fault occurs in the unit or equipment there is a possibility of electric shock.
What should consumers do?
Cease using the product immediately. Customers should return their unit to the Total Tools store where purchased for rectification of the defect.
Traders who sold this product
37 Total Tools franchised stores
Where the product was sold
Australian Capital Territory
New South Wales