Vigilant F3200 Fire Indicator Panel MAF/PSU Module Fitted with "Dong Woo" Signalling Relays manufactured during 2005-2007 inclusively.
What are the defects?
There is the potential for a latent fault to develop within F3200 Fire Alarm panels installed with a MAF/PSU module fitted with "Dong Woo" brigade signalling relays.If the fault develops and the relay fails, the fire alarm panel will fail to send an automated signal to the fire department and/or monitoring centre that the fire alarm has been activated.
What are the hazards?
What should consumers do?
Contact Tyco F3200 Customer Service on 1300 721 517 for a Return Authorisation Number (RAN) and a claim form. Complete the claim form and return to the address listed on the top of the claim form.
Tyco Australia Pty Ltd
Where the product was sold
Dates available for sale